Not many steam systems in at the Jersey shore so I was surprised when he called, but wasn’t surprised he couldn’t find any local plumbers to do the replacement. It was a Utica PEG150 375 sq ft connected to 540 sq ft of radiation, needless to say it didn’t work. The house was also piped in all 3” steam mains. Not sure why but I guess someone had some money to spend back in the day. I went back and forth between the EG65 and the EG55 ultimately I decided to go in with the EG55 figuring it’s almost 700 sq ft with the pickup factor added.
Doing this job by myself so I’m beat up right now.