Welcome! Here are the website rules, as well as some tips for using this forum.
If you've found help here, check back in to let us know how everything worked out.
It's a great way to thank those who helped you.
How some pros install and professionals accept
I was asked to check on the two boilers and 3 storage tank installation at a new student residence. This was an engineered job. The engineer said the install was correct. There was two 500,000 BTU boilers connected together on 1 1/2 pipe as well as the three tanks. Failure 1, pipe sizing to small for 100 GPM. Failure 2, the small Taco pumps could pump 20 GPM if there was no boiler restriction. Plumber redid the piping and installed the correct model Grundfos pumps. Failure 3, look how the pumps were installed. One already was making noise.