Welcome! Here are the website rules, as well as some tips for using this forum.
If you've found help here, check back in to let us know how everything worked out.
It's a great way to thank those who helped you.
Is my circulator undersized?
On Christmas day my boiler pump started making a terrible racket.
Turned out it was a failed coupler on my B&G Series 100 NFI.
I had a spare pump, a B&G NRF-22 that came with the new boiler I installed in 2010, and that I had set aside for just this situation.
This new NRF-22 pump seems to be doing fine, but is it a good fit for my needs?
On paper this pump might be undersized for my converted gravity system.
My system has three zones (one pump, three zone valves):
Zone1 - EDR=112.2 GPM=2.7 (first floor FR and kitchen)
Zone2 - EDR=299.6 GPM=7.5 (first floor LR, DR, Foyer, finished basement)
Zone3 - EDR=496.2 GPM=11.6 (second and third floor, 8 rooms)
Total - EDR=908.2 GPM=21.3
EDR was calculated by adding the values for all the radiators in my system.
The GPM values are extrapolated from a table posted in a previous Wall post:
According to this post, the NRF-22 has these maximum values:
NRF-22: GPM=17 EDR=725
Thing is, the system load depends on which zones are calling for heat.
Should I move up to a higher capacity pump like the B&G NRF-33?
Or are there better choices out there?
The NRF-22 does sound like a cheap timer.