Welcome! Here are the website rules, as well as some tips for using this forum.
Need to contact us? Visit https://heatinghelp.com/contact-us/.
Click here to Find a Contractor in your area.
Using Nest with air handlers
samosa Member Posts: 2
I have 2 Mitsubishi unit sez kd12na4r1.th each connected to it's own nest thermostat in our house. I am having issue cooling the house down as it constantly stays at 70f during the course of the night. Do I need to play with settings
EdTheHeaterMan Member Posts: 5,310This Mitsubishi unit is not compatible with Nest Learning Thermostats. the indoor and outdoor units communicate with a 2 or 3 wire communication protocol. There should be a Mitsubishi wired remote control that acts as a thermostat on your wall.
Nest thermostat is designed for non communicating systems that use industry-standard wiring that operates relays as follows:
R terminal is for 24v. AC power
C terminal is for 24v. AC common
Y terminal is connected to R on a call for cooling
W terminal is connected to R on a call for heat
G terminal is connected to R on a call for fan operation
The heat pump operation is slightly different. but uses the same principle to connect R terminal to various other terminals or operate reversing valve solenoid and relays for fan and compressor.
I'm interested in how you connected the Nest to the Air handler?!?Edward F Young. Retired HVAC ContractorSpecialized in Residential Oil Burner and Hydronics0
samosa Member Posts: 2I used Mitsubishi PAC-US444CN-1 along with
RIAD MAGNETICS VPL24-2100
- 120.8K All Categories
- 83.8K THE MAIN WALL
- 2.8K A-C, Heat Pumps & Refrigeration
- 53 Biomass
- 416 Carbon Monoxide Awareness
- 36 Chimneys & Flues
- 1.7K Domestic Hot Water
- 4.7K Gas Heating
- 116 Geothermal
- 154 Indoor-Air Quality
- 2.9K Oil Heating
- 49 Pipe Deterioration
- 753 Plumbing
- 5.3K Radiant Heating
- 358 Solar
- 13.9K Strictly Steam
- 3K Thermostats and Controls
- 50 Water Quality
- 622 Buy, Sell, Barter
- 37 Industry Classes
- 70 Job Opportunities
- 14 Recall Announcements