Welcome! Here are the website rules, as well as some tips for using this forum.
Need to contact us? Visit https://heatinghelp.com/contact-us/.
Click here to Find a Contractor in your area.
Nest E thermostat wiring
So I have a nest e but I’m getting an error for the red wire not being connected. My current thermostat has a white, red, and blue. After checking the wiring downstairs I found the problem but wanted to get confirmation here first. The blue and red are tied together see pictures. Please advise on how I can get this right.
The Colors are irrelevant, the electricity does not know the difference. Can you draw out which wires go where? What type of t-stat is pictured?"If you can't explain it simply, you don't understand it well enough"
It’s a basic Honeywell as seen below. The white is just 2 tied together to extend it and the blue/red are tied together to extend it too? The brown sheathed covered wires are going to the furnace and the white/blue are coming from thermostat upstairs.0
The nest will want the R and W which are connected to the TT in your picture. It will also want a common wire. I am guessing that the 3rd wire is a common. I would double check before connecting."If you can't explain it simply, you don't understand it well enough"
Nest , slowly I turn ....step by step .
The nest needs to be powered all the time , normal problem you need a third wire to hard wire a common . You have an option to pull it off the wall and charge it with that tripod adapter ..I have enough experience to know , that I dont know it all0
As I read the directions for the Nest -- which, in my not at all humble opinion, are even worse than the thermostat itself -- you can use that blue wire as a common power source. Question is, where to hook it up. That controller on your system does not have a handy dandy common terminal. What it expects is a switch which closes the circuit between the two T terminals.
I think that that switched circuit would be Rc and W on the Nest; thing is, the Nest is going to expect 24 vac between the common and Rc, and you may have to wander around in the basement to find a power source.
Incidentally, I hope whoever did that wiring in the basement for the thermostat never returns. That's just... horrible.Br. Jamie, osb
Building superintendent/caretaker, 7200 sq. ft. historic house museum with dependencies in New England0
- 121.3K All Categories
- 84K THE MAIN WALL
- 2.9K A-C, Heat Pumps & Refrigeration
- 53 Biomass
- 417 Carbon Monoxide Awareness
- 40 Chimneys & Flues
- 1.7K Domestic Hot Water
- 4.7K Gas Heating
- 119 Geothermal
- 155 Indoor-Air Quality
- 3K Oil Heating
- 56 Pipe Deterioration
- 771 Plumbing
- 5.4K Radiant Heating
- 362 Solar
- 14K Strictly Steam
- 3K Thermostats and Controls
- 51 Water Quality
- 625 Buy, Sell, Barter
- 38 Industry Classes
- 73 Job Opportunities
- 17 Recall Announcements