Welcome! Here are the website rules, as well as some tips for using this forum.
Need to contact us? Visit https://heatinghelp.com/contact-us/.
Click here to Find a Contractor in your area.
Looking for some help!
Hello all excited to be here and ready to listen! I have a 2 pipe direct return setup to a natural gas Williamson boiler in my home. I have what I believe to be 3” supply cast iron piping and 2” return piping. I will be doing the work myself. I have a couple of questions.
1st- I’d like to remove the cast iron piping in my basement and replace with copper piping or pex to allow for headroom. Is this feasible and if so what size piping do I need? 2nd- I’d like to create 2 zones for upstairs and downstairs. I’m an HVAC mechanic so I’m not afraid of wiring and installing pumps and zone valves. Again is this feasible?
Sorry for the long post but I’m ready to listen to the pros here and am excited to get started. Let me know what other details I need to provide!!!
That sounds as though once upon a time it was a gravity circulation system. They're wonderful... it certainly is feasible to convert that to a forced circulation system with smaller pipes. The pipe size would depend on the BTUh load which the pipe is service.
You will certainly need some sort of manifold, though, and balancing valves, or the balance between various radiators and upstairs and downstairs etc. will be way off.Br. Jamie, osb
Building superintendent/caretaker, 7200 sq. ft. historic house museum with dependencies in New England2
In this scenario, you're gonna have to look at removing all of the old mains in the basement or else you'll have a balancing problem as Jamie mentioned.
The be best approach may be to connect properly sized pex-al-pex to each individual riser and connect them to a good manifold like a Caleffi, Rehau, Viega.
You can install actuators on the manifold for each rad that could be controlled by different thermostats. However, a better approach would be to put TRVs on each rad and run the system on constant circulation with a delta P circulator.Bob Boan
You can choose to do what you want, but you cannot choose the consequences.2
- 121.3K All Categories
- 84K THE MAIN WALL
- 2.9K A-C, Heat Pumps & Refrigeration
- 53 Biomass
- 417 Carbon Monoxide Awareness
- 40 Chimneys & Flues
- 1.7K Domestic Hot Water
- 4.7K Gas Heating
- 119 Geothermal
- 155 Indoor-Air Quality
- 3K Oil Heating
- 56 Pipe Deterioration
- 769 Plumbing
- 5.4K Radiant Heating
- 362 Solar
- 14K Strictly Steam
- 3K Thermostats and Controls
- 51 Water Quality
- 625 Buy, Sell, Barter
- 38 Industry Classes
- 73 Job Opportunities
- 17 Recall Announcements