Welcome! Here are the website rules, as well as some tips for using this forum.
If you've found help here, check back in to let us know how everything worked out.
It's a great way to thank those who helped you.
I have a 3 year old cga that I am taking out of a customers house. Like I said irs only three years old, one of my friends wants it but it’s just a little bit oversized. What’s involved in reducing the gas input/ output? Is it as simple as blocking off a burner. Is that going to effect the flow size? Hypothetical the existing boiler is 102 output and I only need 75, how would you go about doing this?