Welcome! Here are the website rules, as well as some tips for using this forum.
If you've found help here, check back in to let us know how everything worked out.
It's a great way to thank those who helped you.
We were called in to take a look at the endless issues plaguing this boiler issues with the system.
Found that the near boiler piping was all wrong as you will see in the pictures. The boiler would short cycle like mad and whenever the boiler would go for trial for ignition there would be a very boom which was clearly due to improper flue and air intake pipe size.
We added a buffer tank to stop the boiler from short cycling and power flushed out all debris that was in the system.
Creative Solutions Plumbing & Heating LLC
Co-Owners: Fred Drescher, Jr & Eliezer "Ezzy" Travis
Marketing & Operations: Dawn Drescher
201.499.0223Follow us on Facebook.
Check us out on Instagram: creative_solutions519