Welcome! Here are the website rules, as well as some tips for using this forum.
If you've found help here, check back in to let us know how everything worked out.
It's a great way to thank those who helped you.
Winter return repipe project
The more I look at the end of my main, the more I don't like it. It cuts across one side of my basement to the boiler which is centrally located. At 64 inches off the floor, it is a perfect height to smack my forehead. And it adds 10 feet of travel to the main vent that isn't necessary.
Instead I want to drop it right after the last radiator runout, and make it a wet return that runs on the floor. I'll put wooden ramps on either side of it to minimize the trip hazard and protect the line. Have a look at the attached drawing that I think shows everything.
My main question is: copper or steel? I don't mind working with the steel and I don't think either will rot out before I do (ha!)
The existing end of the main is 1" and so is the wet return. Would that be an OK size or should I up it to 1-1/4?
My last question is: does anyone see any reason why not? Thanks all, and let me know if I left anything out.
1 pipe Utica 112 in Cedar Grove, NJ, 1913 coal > oil > NG