Welcome! Here are the website rules, as well as some tips for using this forum.
If you've found help here, check back in to let us know how everything worked out.
It's a great way to thank those who helped you.
Troubleshooting a some finicky 2nd fl radiators in a 1929 single-pipe system. Pictures included.
Hi, this is my first post, but I've been reading for a while. I have a 1929 house with single-pipe steam in New Jersey, and I've been trying to get it working efficiently and flawlessly. Last winter I built an antler with one Barnes and Jones BigMouth on it to replace an ancient main vent with a little pinhole at the top. I don't know if it worked, but I figured more air out, faster, would be best. I built the antler with the ability to add on to it. With an 80ft, 2" pipe that runs in a circuit around the basement, does it sound like I did ok, or do I need more? I have a reason for asking this, but I'll get to that probably in another thread.