Welcome! Here are the website rules, as well as some tips for using this forum.
If you've found help here, check back in to let us know how everything worked out.
It's a great way to thank those who helped you.
Utica peg187eid won't turn on after surge
Hey folks - hoping to get some tips!
We recently had a nearby lightning strike. It killed about 10 LED bulbs, 2 dimmer switches and a surround sound received.
About a week after that, I decided to test the boiler. The thing wouldn't come on.
I'm in central Illinois - no one seems to know how to work on these things. Got a tech to come out, he thought it was the CycleGuard based on its output. LED indicators looked good though. He took a week to get back with a price (despite me calling daily). Due to the smoothing cold, I ordered the part myself and our it in. No luck.
I think the issue is eather the main control (UTEC 511-330-097) or the Honeywell gas valve (which never clicks). Thoughts?
I'm handy with a multi meter but confused about what I should take. Local guy can't make it back for another few days. Trying to avoid a cold family!! Thanks.
-Ecobee thermostat is calling for heat. Did try bypassing it by shorting T-stat wires at boiler
-cycleguard behaves properly. Tech suspected it wasn't outputting 24v AC to UTEC, my meter agrees but I find the wiring very confusing.