Welcome! Here are the website rules, as well as some tips for using this forum.
If you've found help here, check back in to let us know how everything worked out.
It's a great way to thank those who helped you.
Well this was the first one that I have seen ,I did not install but the original installer from what I was told was there 2 season and added Freon and she was non functional end of last year . So airing to the caution I pressure test found the leak isolated and ensured line set and coil where not a issue also .saddest part is that it would have been warranties but the original installer chose to refill 2 times instead of just trying to get the customer warranty very sad .even through the original coil and line set where good I wanted no issues and did a new line set coil and condenser and of course no micro channel .on a sadder note as with most new equipment there no hi or low pressure controls so the compressor just kept goin doing nothing . saddest part is the other micro channel unit is also developed a leak and of course the warranty is about done and the original installer is not answering calls .i had quoted the job also and they are friends and chose the cheapest price not realizing that there is a difference .on a side note the outdoor unit where not dirty I’m kinda glad I never installed and micro channels and stay away from alum coils except for some trane units and there design is not micro channel but a pia to clean peace and good luck clammy
R.A. Calmbacher L.L.C. HVAC
NJ Master HVAC Lic.
Specializing in steam and hydronic heating