Welcome! Here are the website rules, as well as some tips for using this forum.
If you've found help here, check back in to let us know how everything worked out.
It's a great way to thank those who helped you.
With the help of a coworker, I salvaged an 10 year old 200k BTU input Hydrotherm VGA-200. The home was damaged in a fire 7 months ago and insurance has finally settled so it can be demolished. One less 1 pipe steam system in the area. Probably only 3 or 4 left I’d guess. The boiler were drained so they didn’t freeze. The “scrappers” had already cut it loose and it was laying on it’s side. But case and base is still in good shape other than some rust. Flue damper was in automatic, so I’m hopeful it still works. Flue got crushed, but it’s just 7” galvanized pipe. Collector is OK. Cycleguard is destroyed, but those seem to be universally disliked. Some refractory came off, but I salvaged some from a 2nd 300k boiler. The house had a 2 boiler setup. My company installed them. I als salvaged all the burner tubes from the 2nd boiler and it’s cycle guard LWCO.
Plan is to plug it and fill it for a basic leak check. Will pressurize it if I can get the 3” pipe out of the supply. Have a 3’ pipe wrench. Then get it in the basement and start the project.
Will need to transfer all my intermittent pilot controls, 2 stage gas valve, LWCO and it needs a gauge glass and repair the refractor. The boiler has a single 3” pipe out. I’ll run that vertically about 3-1/2’ then down to a drop header where I’ll connect the existing 3” header then connect the equalizer. I’ll have the brush the flue as they have a light surface coating of rust from the damp basement. And clean up the burners and pick the 5 best looking ones of the 12 I have.
Last, I’ll get it setup to eventually add a hot water loop for a indirect tank.
Dry return will get two 2”x3/4” fittings for maximum venting.
Also found a very clean Detroit Radiator valve and couple wood knobs to replace some of mine. Grabbed a transformer and a contractor too.
Should be fun. Worst case, they only last a couple years, but the header will better fit the height of modern boilers in the correct size. Current boiler is not only oversized, there’s no equalizer and it’s supposed ot have a 2nd supply. I’m losing about 2 gallons of water a week. Not extreme for a nearly 20 gallon volume boiler, but it’s 36 years old and cement between sections is falling out, burner box leaks a little because of it, insulation is in bad shape and burners are pretty rusted and just galvanized not SS. Gas analyzier shows 75% effeceincy,