Welcome! Here are the website rules, as well as some tips for using this forum.
If you've found help here, check back in to let us know how everything worked out.
It's a great way to thank those who helped you.
Update: Curious about Cause of Flooded Steam Boiler
Click here for original post.
We received another no heat call, and again the pump was running. The boiler was also flooded again. I carefully removed the cover of the MM150S level control. I found that the float was up and the lever of the switch was completely depressed. A small bump to the switch and the pump stopped. We replaced the head of the MM150S and all is well again.