Welcome! Here are the website rules, as well as some tips for using this forum.
Update: Curious about Cause of Flooded Steam Boiler
Click here for original post.
We received another no heat call, and again the pump was running. The boiler was also flooded again. I carefully removed the cover of the MM150S level control. I found that the float was up and the lever of the switch was completely depressed. A small bump to the switch and the pump stopped. We replaced the head of the MM150S and all is well again.