Welcome! Here are the website rules, as well as some tips for using this forum.
Need to contact us? Visit https://heatinghelp.com/contact-us/.
Click here to Find a Contractor in your area.
Curious about Cause of Flooded Steam Boiler
This fall we installed a Weil-McLain LGB-7 steam boiler. We used a McDonnell Miller #150S level control connected to a duplex boiler feed tank. (We only run one pump at a time.) The boiler was cleaned, skimmed, and then maintained with Romar 903 chemicals. All was well, until...
The other day we received a no heat call from the boiler owner. When I got there, the boiler feed pump was running non-stop. The system was flooded.
I shut off the power to the pump and water gushed out of the overflow as expected. I took the cover off of the MM150. Everything was normal. The float was up. There was no continuity through the switch. The pump was within the specifications of the switch.
This system has 2 - 4" zone valves. My questions are these: Is it possible to air lock the float chamber of the 150, even if it's properly piped? Could a vacuum from the zone valves have affected the float?
Curious to find an answer.
- All Categories
- 84.4K THE MAIN WALL
- 3K A-C, Heat Pumps & Refrigeration
- 53 Biomass
- 417 Carbon Monoxide Awareness
- 44 Chimneys & Flues
- 1.8K Domestic Hot Water
- 4.8K Gas Heating
- 120 Geothermal
- 156 Indoor-Air Quality
- 3.1K Oil Heating
- 57 Pipe Deterioration
- 801 Plumbing
- 5.5K Radiant Heating
- 372 Solar
- 14.1K Strictly Steam
- 3.1K Thermostats and Controls
- 54 Water Quality
- 635 Buy, Sell, Barter
- 39 Industry Classes
- 81 Job Opportunities
- 22 Recall Announcements