Welcome! Here are the website rules, as well as some tips for using this forum.
If you've found help here, check back in to let us know how everything worked out.
It's a great way to thank those who helped you.
Now that the boiler is all working again, I was wondering what the normal cycle of the boiler is supposed to be? Right now, i call for heat, all Rads get steam and heat up pretty quick. Probably with 10 - 15 min cold start boiler to hot Rads. the pressure of the system starts to pick up and in about 20 min, I hit 5 PSI and the pressuretrol kicks in a shuts her down. After about 2 minutes, the pressure comes down enough and the boiler kicks back on for about 5 min before it hits the 5 PSI again.
I'm positive that this boiler is oversized. Few things happened to lead to this. First, Plumber that had no idea what he was doing. Replaced an oil fired Weil for this Gas fired IN6. He never actually did the calculations, just looked at the old oil fired and replaced with the same load.
In addition, dealt with an idiot of a contractor during my kitchen renovation in which he just removed two rads and didnt replace them with anything.
Right now, whole house has 6 Rads on an IN6. I'm sure this is not sized properly. Someone told me that an IN6 can handle 11 rads or so.
I'm just wondering how bad of a spot im in right now.