Welcome! Here are the website rules, as well as some tips for using this forum.
Need to contact us? Visit https://heatinghelp.com/contact-us/.
Click here to Find a Contractor in your area.
Circulator placement in relation to elbows etc.
Solid_Fuel_Man Member Posts: 2,575
Where is the best place (how far) for a circulator to be in a circuit in relation to flow restrictions like elbows Ts, flow-checks etc? Is it advisable to have an elbow 10 pipe diameters before the inlet of a circ? What about after? Is there a rule of X number of pipe diameters as best practice or is it irrelevant in small resi. systems with flows under 15GPM? How important is laminar flow and where in the piping in relation to the circulator?
Thanks in advance!
Thanks in advance!
Serving Northern Maine HVAC & Controls. I burn wood, it smells good!
I like this one from ME"If you can't explain it simply, you don't understand it well enough"
That's a good one.Zman said:
I like this one from ME
One that I have run into on occasion is covered, but not specifically.
With a horizontal run, turning down to a boiler, keep the 4 pipe diameters distance. If you make it a close connection with a tee into a boiler with another boiler below it, the turbulence of the laminar flow water trying to change to circular will drop the pressure and the water may not flow into the second boiler. No matter how big a pump you install. It will never be shown on a drawing like that. Just in the agony of the install. Trying to get 10# of boilers and piping into a 5# space,
- 120.9K All Categories
- 83.9K THE MAIN WALL
- 2.8K A-C, Heat Pumps & Refrigeration
- 53 Biomass
- 415 Carbon Monoxide Awareness
- 34 Chimneys & Flues
- 1.7K Domestic Hot Water
- 4.7K Gas Heating
- 114 Geothermal
- 154 Indoor-Air Quality
- 3K Oil Heating
- 49 Pipe Deterioration
- 756 Plumbing
- 5.3K Radiant Heating
- 358 Solar
- 13.9K Strictly Steam
- 3K Thermostats and Controls
- 50 Water Quality
- 619 Buy, Sell, Barter
- 37 Industry Classes
- 70 Job Opportunities
- 14 Recall Announcements