Welcome! Here are the website rules, as well as some tips for using this forum.
Need to contact us? Visit https://heatinghelp.com/contact-us/.
Click here to Find a Contractor in your area.
GHAYESQUALITYAIR Member Posts: 1
I'M WORKING ON 150K BTU BOILER SYSTEM THATS SUPPLING TWO HOMES THE FIRST IS THREE STORIES THE SECOND IS TWO STORIES.THIS SYSTEM ALSO HAS BASEBROAD RADS CONNECTED INTO THE SYSTEM WITH PURGE VALVES.THE RADIATORS ON THE FIRST FLOORS ARE HOT HEATING,THE SYSTEM IS OLD AND IT HAS BEEN FLUSHED SERVERAL TIMES AND BLEED ALSO.
What's your question?
You haven't stated a problem or asked any questions.
Also, please turn the "caps lock" off on your keyboard. All caps means you're shouting.Bob Boan
You can choose to do what you want, but you cannot choose the consequences.0
may be the radiators are not heating on the first floor after purging. Dont know which structure or both has the problem though.0
how to fill
How did you flush your system ? Are you certain you purged the cold rads? Where is the expansion tank ?0
All caps means you're shouting.
;-) HA HA.... I had to turn my speaker's volume down when I read this thread!0
This discussion has been closed.
- 120.8K All Categories
- 83.8K THE MAIN WALL
- 2.8K A-C, Heat Pumps & Refrigeration
- 53 Biomass
- 416 Carbon Monoxide Awareness
- 33 Chimneys & Flues
- 1.7K Domestic Hot Water
- 4.7K Gas Heating
- 114 Geothermal
- 154 Indoor-Air Quality
- 3K Oil Heating
- 49 Pipe Deterioration
- 745 Plumbing
- 5.3K Radiant Heating
- 358 Solar
- 13.9K Strictly Steam
- 3K Thermostats and Controls
- 50 Water Quality
- 622 Buy, Sell, Barter
- 37 Industry Classes
- 70 Job Opportunities
- 14 Recall Announcements