Welcome! Here are the website rules, as well as some tips for using this forum.
Need to contact us? Visit https://heatinghelp.com/contact-us/.
Click here to Find a Contractor in your area.
Hi. I was recently performing a maintenance on at AO Smith BTH400 Cyclone. I don’t normally do a combustion but I decided to do one cause I suspected it wasn’t running right.
As suspected, I found my O2 very low at 1.9. Gas pressures are within range. No more than 1.5” drop. I used the regular gas adjustment to adjust my o2 up to 5.
There is an offset adjustment on this gas valve and I can’t figure out how to use it. Instruction don’t really explain it well.
Has anyone have any experience with these gas valves?
More specifically, using the offset adjustment?
- 117.8K All Categories
- 82.9K THE MAIN WALL
- 2.7K A-C, Heat Pumps & Refrigeration
- 44 Biomass
- 406 Carbon Monoxide Awareness
- 10 Chimneys & Flues
- 1.6K Domestic Hot Water
- 4.3K Gas Heating
- 107 Geothermal
- 149 Indoor-Air Quality
- 2.7K Oil Heating
- 45 Pipe Deterioration
- 696 Plumbing
- 4.9K Radiant Heating
- 353 Solar
- 13.3K Strictly Steam
- 2.9K Thermostats and Controls
- 48 Water Quality
- 601 Buy, Sell, Barter
- 31 Industry Classes
- 65 Job Opportunities
- 12 Recall Announcements