Welcome! Here are the website rules, as well as some tips for using this forum.
If you've found help here, check back in to let us know how everything worked out.
It's a great way to thank those who helped you.
Dayton 3UH62 furnace house blower not working.
Blower motor was going out on our furnace, ordered a matching Protech motor as a replacement along with a new run capacitor. Finished it up last night and went to test it. Exhaust blower kicks on then the burners light. The house blower never kicks on, which I assume triggers a high temp limit shutting the burners off. The green OK light on the board is flashing in a three blink pattern, I am assuming this is a fault code for a temp limit but cannot find the definitions for the codes. Any ideas on A reason the new motor is not turning on?