Welcome! Here are the website rules, as well as some tips for using this forum.
Need to contact us? Visit https://heatinghelp.com/contact-us/.
Click here to Find a Contractor in your area.
Rinnai vs. Burnham Alpine 95% boiler
in Gas Heating
I am looking to replace our 20 yr old (propane) boiler with a 95% efficient condensing boiler. I have 3 quotes, the 2 I am considering are for a Rinnai wall mounted unit and a Burnham Alpine floor mounted unit. System is forced hot water, 4 zones. I am trying to compare what seems like apples and oranges. Help / feedback is appreciated. Thanks
Have any of the contractors done a Heat Loss of the home to properly size the boiler? When going to a mod/con boiler, size is critical.0
They both estimated at 150,000 BTU. Is a heat loss analysis the same as measuring the baseboards? If not, how is it done?
Any feedback on Rinnai vs. Alpine?0
Slant/Fin has a download for a heat loss calculator. Just out of curiousity, and not a perfect determining factor....how many sq/ft is your home? http://www.pvsullivan.com/Downloads.html0
we are approx 3100 square ft0
You do the Heat Loss. The difference between, say 120 and 150000btus, when it comes to a mod/con is huge. The boiler will not function properly if over-sized. It is a completely different concept than the old way of heating a home....blast a lot of heat to the baseboards then shut off and wait to do the same thing. With the mod/con it produces just enough heat to counteract the outside temperatures. Longer burn times with lower flames keep the boiler condensing, and that is when it is most efficient.It wouldn't make much sense to comment on one boiler,over the other, if neither was correct for you. You have 1 chance to get the boiler sized correctly, if you don't get it right, you might as well stand next to the boiler every day, and burn a $5 or $10 bill.0
How have you arrived at Rinnai and Burnham?
Rinnai's exchanger is fairly new, I would like to see how it performs in the real world before I pass judgement.
Burnham is still using the Gionni exchanger. They require fairly large circulators and diligent maintenance to run correctly.
I only install firetube HX. Triangle tube and Lochinvar both use them. They are an excellent low maintenance exchanger.
Carl"If you can't explain it simply, you don't understand it well enough"
Rinnai v. Burnham
I received 3 quotes. Burnham Alpine was from the current company we use for service. #2 was from Sears via Service Magic, who quoted a Dunkirk which I believe is also made by Burnham. I don;t trust Sears for customer service after the sale so I have pretty much ruled them out. #3 was also referred by Service Magic and they are quoting the Rinnai unit.
Still pretty lost at this point. Alpine is the cheapest, which is where I'm leaning unless there is a good reason anyone can offer otherwise. Thanks0
If it happens to be a Helix VLT, it has a fire-tube HX and I'd give that serious consideration.0
This discussion has been closed.
- 120.9K All Categories
- 83.8K THE MAIN WALL
- 2.8K A-C, Heat Pumps & Refrigeration
- 53 Biomass
- 416 Carbon Monoxide Awareness
- 36 Chimneys & Flues
- 1.7K Domestic Hot Water
- 4.7K Gas Heating
- 116 Geothermal
- 154 Indoor-Air Quality
- 2.9K Oil Heating
- 49 Pipe Deterioration
- 754 Plumbing
- 5.3K Radiant Heating
- 358 Solar
- 13.9K Strictly Steam
- 3K Thermostats and Controls
- 50 Water Quality
- 622 Buy, Sell, Barter
- 37 Industry Classes
- 70 Job Opportunities
- 14 Recall Announcements