Welcome! Here are the website rules, as well as some tips for using this forum.
If you've found help here, check back in to let us know how everything worked out.
It's a great way to thank those who helped you.
I dont service A/C, but...
I normally dont service A/C, but a friend called, and said she was having a problem with her cooling. The second floor was doing great, but the first floor just wouldn't get comfortable. I asked her where her thermostats were set, and if they were on "cool" (T-87F, with heat/cool plate). She said she was set on 74, and yes, she was on cool. I went over to take a look. Her 2nd floor thermostat was a heat/cool, controling forced hot water baseboard for the 2nd floor, and A/C for the whole house. Her first floor thermostat controlled the baseboard on the first floor. Both were set at 74*F. The A/C was fighting the baseboard. This will probally explain her next question, about her gas bill being higher than she expected this summer.
She purchased the house from a builder about 10mths ago. I don't think anyone bothered to explain the operation of the heating and cooling systems to her. Just grabed her 300K and walked away.
<A HREF="http://www.heatinghelp.com/getListed.cfm?id=143&Step=30">To Learn More About This Contractor, Click Here to Visit Their Ad in "Find A Contractor"</A>