Welcome! Here are the website rules, as well as some tips for using this forum.
If you've found help here, check back in to let us know how everything worked out.
It's a great way to thank those who helped you.
Single loop single pump snowmelt
The typical system I've seen uses a primary secondary loop, along with a condensing boiler and glycol as needed.
With a good condensing boiler that can take very cold return temps is it any advantage to run a single loop and a single pump?
Does the viscosity of glycol require the primary/ secondary loops to keep the gpm high enough when the system starts cold?