Welcome! Here are the website rules, as well as some tips for using this forum.
If you've found help here, check back in to let us know how everything worked out.
It's a great way to thank those who helped you.
Hi. My existing steam piping is all 2”, the replacement Peerless 63-04 states the Header single feed needs to be 2 1/2”. Is there any potential issue putting a 2 1/2” x 2” x 2 1/2” tee on the header to connect vertically to the existing 2” system?
Thanks in advance.