Welcome! Here are the website rules, as well as some tips for using this forum.
Need to contact us? Visit https://heatinghelp.com/contact-us/.
Click here to Find a Contractor in your area.
do these F&T traps fail open or closed?
Most of the steam traps on my radiators are of this type (they have thermostatic disc inside).
I read on this site that the only way to test them is to open the output side while in operation and if you have steam coming out, it's bad.
However, what if it fails closed? How would you know it's bad?
- All Categories
- 84.3K THE MAIN WALL
- 3K A-C, Heat Pumps & Refrigeration
- 53 Biomass
- 417 Carbon Monoxide Awareness
- 44 Chimneys & Flues
- 1.8K Domestic Hot Water
- 4.8K Gas Heating
- 120 Geothermal
- 156 Indoor-Air Quality
- 3K Oil Heating
- 57 Pipe Deterioration
- 798 Plumbing
- 5.4K Radiant Heating
- 371 Solar
- 14.1K Strictly Steam
- 3.1K Thermostats and Controls
- 54 Water Quality
- 634 Buy, Sell, Barter
- 39 Industry Classes
- 80 Job Opportunities
- 22 Recall Announcements