Welcome! Here are the website rules, as well as some tips for using this forum.
Need to contact us? Visit https://heatinghelp.com/contact-us/.
Click here to Find a Contractor in your area.
oilfurnace beckett with pump issue
in Oil Heating
my oil furnace runs and gives me red light every few days and i bleed oil few 30 sec and system runs fine and again does the same thing every few day.i check all things and i can not fix it . and someone suggested that i should check my fuel pump screen/filter and gasket (pump suntec A2VA-7116.) SO I changed the screen/filter and gasket on my oil pump and now i have no oil coming from bleeder valve. any suggestion .
There are so many possibilities... I'm sorry to have to say this, but I really can't recommend trying to diagnose and repair an ailing oil burner to someone without the necessary training and tools. So... if you want my advice, it's call a pro. time.Br. Jamie, osb
Building superintendent/caretaker, 7200 sq. ft. historic house museum with dependencies in New England2
Did you put the pump screen gasket back on in the right orientation, and correctly?
Initially it sounds like a vacuum leak, losing it's prime. But it could also be a restriction, and every time you open the bleeder it releases the restriction. It could also be your fuel pump is failing, specifically the cut-off is bad. Or a combination of the 2.
Checking with pressure & vacuum gauges can help pinpoint the issue by your service provider.
And a proper cleaning/PM and set up with a full combustion test would help.steve1
to Steve i did not know it has some kind of orientation when putting it back. i will check. it definitely vacuum leak issue. cuz oil tank is full and it only happened after screen change.
to Alan yes my pump pulls the oil from the tank main oil hose is form top and did change the oil filter on tank week ago think that will fix the issue. but now after changing screen and gasket i think i have vacuum leak . it not pulling the oil from tank.0
Thanks. my pump was on last leg.. i changed the oil pump and system worked fine..thanks again0
- 121.3K All Categories
- 84K THE MAIN WALL
- 2.9K A-C, Heat Pumps & Refrigeration
- 53 Biomass
- 417 Carbon Monoxide Awareness
- 40 Chimneys & Flues
- 1.7K Domestic Hot Water
- 4.7K Gas Heating
- 119 Geothermal
- 155 Indoor-Air Quality
- 3K Oil Heating
- 56 Pipe Deterioration
- 768 Plumbing
- 5.4K Radiant Heating
- 362 Solar
- 14K Strictly Steam
- 3K Thermostats and Controls
- 51 Water Quality
- 625 Buy, Sell, Barter
- 38 Industry Classes
- 73 Job Opportunities
- 17 Recall Announcements