Welcome! Here are the website rules, as well as some tips for using this forum.
If you've found help here, check back in to let us know how everything worked out.
It's a great way to thank those who helped you.
Pensotti Panel Radiator Replacing 17' of Slant Fin 30
Now I am considering replacing 17' of Slant Fin baseboard with a Pensotti 24 x 44 double radiator. It would be the first in a series loop containing another 12' of fin tube after the Pensotti. Can I just pipe with reducers 3/4"to 1/2" and be okay? I looked at their formulas for determining pressure drop, and it is a bit confusing to me. As usual, any help would be appreciated.