Welcome! Here are the website rules, as well as some tips for using this forum.
So I have a two pipe steam heat. At the end of the return line are two f & t traps. one coming from one half of house. The other coming from other half of house. Only one return line has Hoffman 74 vent? Shouldn't the other line have a main vent as well?