Welcome! Here are the website rules, as well as some tips for using this forum.
If you've found help here, check back in to let us know how everything worked out.
It's a great way to thank those who helped you.
matching suppy and return size
I have 1 unit apt. with forced air heat.Furance is in basement. Some rooms have 2 supply lines with floor vents and some have one. The return is one floor return in a room without supply line( kitchen). I would like to add cold air returns in as many rooms as possible. I have read using floor joists is not the right way to go because hard to get good seals.Should returns pipe sizing match supply size?? example. if room feed with 2- 6" duct it looks like 1-8" return would handle about the same volume of air. any thoughts??
round vs. Rectangular piping
tin vs. flexible insulated tubing??