Welcome! Here are the website rules, as well as some tips for using this forum.
If you've found help here, check back in to let us know how everything worked out.
It's a great way to thank those who helped you.
Burnham ES27 no heat - FIXED!!
Woke up to a cold boiler (Burnham ES27).
The boiler reports the following on the IQ Boiler Control:
StA (Status) 1 Standby
hr (Heat Request) OFF
The system though is calling for heat (through TT terminals on IQ Option Board).
The Option Board connects with a wiring harness to the IQ Boiler Control.
I swapped out the IQ Boiler Control with a spare - same results.
So that leaves either the wiring harness, or the IQ Option Board (neither of which I have spares for).
The boiler was installed in 2011 and has been reliable until now.
Anyone got any ideas for troubleshooting this?