Welcome! Here are the website rules, as well as some tips for using this forum.
If you've found help here, check back in to let us know how everything worked out.
It's a great way to thank those who helped you.
how underfired is too underfired and how to be sure piping is the cause
Bought a house two months back and it came with a Weil-Mclain HE-5 series 3 propane boiler with an a.g.a input of 133k BTU/hr. Even when the tank is full, on a day with a temperature above freezing, the inlet pressure to the boiler's gas valve sits at 9.1 inWC when operating. The manufacturer's stated range for inlet pressure is a minimum of 11 and 13 max. The manifold pressure sits at 8.6 inWC, and should be 10. I don't think that the white-rogers 36c74 is designed to lower the pressure reduction any less than the 0.5 it already is, and I obviously do not wish to crank on the adjument screw to find out.
The 120 gallon tank's regulator is a non-adjustable Fisher Controls R232-BBF, which I don't believe is the issue (although I have not attempted to check the line pressure at the tank end while under load).
My money is on the piping as the cause, but I assume there's some math involved to know for certain. The boiler is the only appliance on the tank, and the piping consists of 6 feet of 21mm outer-diameter black pipe at the boiler end (am assuming SCH 40 1/2"), and 20 feet of 15mm outer-diameter copper tubing back to the tank (am assuming 1/2"), making many sharp bends along the way.
My assumption is that this boiler has been operating this way since it was installed (back in the 1980's?). The air being non-adjustable, manifold pressure would seem to be fairly important. But just how off is off enough to be worried about? A combustion test at the outside vent gave these readings: