Welcome! Here are the website rules, as well as some tips for using this forum.
If you've found help here, check back in to let us know how everything worked out.
It's a great way to thank those who helped you.
Strange hw heating system
Just looked at a boiler replacement n I’m just starching my head Roughly 2800 sq ft home old hydrothermal 134 Mbtu input 117 out nothing weird but here’s where it gets weird right at the boiler reduced to 3/4 both s n r n all 3 zones are 1/2 aquastat set at about 200 degrees. Oh yeah no pump relay just a 10 ft on baseboard mounted on the wall behind the boiler aside from the stats opening zones there’s no pump relay n end switches are wired to nothing. The circ operates by a switch n run constant boiler cycles on temp constantly What crap Thinking of installing a turbo max 24 and setting it up to maintain n just pull heat from the turbo max Maintain the turbo max at 200 n let the heat pull out of the tank What’s your thoughts I have only seen one other system w baseboard simalar to this of course its bout a 5 miles away. The other job I had to completely redo ho could not take the ghosting stain on the walls the only difference is that ones aquastat was set to like 215 n heat didn’t cut it at 190 so it was a total repipe w new baseboard Must have been the same guy Can’t make this junk up what’s the thoughts on using a turbo as a buffer n just maintain peace and good luck clammy
R.A. Calmbacher L.L.C. HVAC
NJ Master HVAC Lic.
Specializing in steam and hydronic heating