Welcome! Here are the website rules, as well as some tips for using this forum.
If you've found help here, check back in to let us know how everything worked out.
It's a great way to thank those who helped you.
Watts 174A Pressure Valve Seeping?
We built a home in the Colorado mountains 14-years ago. Radiant heat on main floor, baseboard on 2nd floor, Dow. 11’ height between bottom of boiler and baseboard. We have a continuing problem with random puddles of glycol seeping from the Watts 174A 30lbs. pressure relief valve. The valve has been replaced 3 times, along with the expansion tank. Original plumbing contractor totally incompetent. Had controls miswired so calling for heat 24-hours a day. Didn’t install shutoff between supply and return manifolds, one zone didn’t work. Plumber could not solve. General found that they installed one loop on supply, the second on the return. So I don’t trust any of their work. They set up system and expansion tank at 14lbs. Cold. It runs about 24lbs. Max. Temp is 180. With everything running. I installed a Watts pressure gauge with a pointer that display maximum pressure. Never over 25lbs. The plumber originally had a glycol mix at 70%. It is now down to 25%. I would appreciate any ideas on troubleshooting and what the cold system pressure should be set at. We are at 8,600’ but I don’t see how altitude would impact pressure. Thank you.