Welcome! Here are the website rules, as well as some tips for using this forum.
If you've found help here, check back in to let us know how everything worked out.
It's a great way to thank those who helped you.
Control for window louver
To pass inspection for my (large) residential boiler, I need to set up the window louver such that the boiler gas burner will not fire unless the louver is open.
My current configuration uses a Belimo control to open the louver when the t-stat calls for heat, but there is no additional control to prevent the boiler firing if the louver does not open successfully.
So two questions: First, any suggestions on the the louver control to use for sensing when the louver is open? And second, any suggestions on how to wire the t-stat, burner, and louver control to meet the condition of not firing the burner if the louver does not open successfully?