Welcome! Here are the website rules, as well as some tips for using this forum.
Is my "standby" Fuel Oil consumption high ???
Have hour meters on burner and circulator. Finally been warm lately so I can get a handle on standby losses, FHW circulator hasn't run for 3 days. So burner is only supplying standby losses and domestic HW. Tankless DHW coil in furnace water jacket
My hour meter on burner has been averaging 0.9 hour/24 hours. 1.1 GPH nossel, so 1.0 gal/24 hours. Does that sound high?
Only two ~ 10 minutes showers per day, and quick handwashing ( two 60 year olds). Old pre 1.1GPM shower heads, 40 psi water. Without old waterpik shower head attached to shower spout flow is ~ 3 GPM on cold water , less on hot (boiler has 5 GPM orfice) Cold water input is 42 deg F.
60 year old National Sunray IV , boiler # 5-19A/O/OP , rated 128k BTU/hr 1.6 gal/hr
Has original burner, National -US model NB2-K2, firing rate .85-2.0 gal/hr, nozzle = 1.10/ 80 deg/ B
Chimney is ~ 4 stories from cellar floor to top. No motorized damper for when burner is off, has barometric damper.