Welcome! Here are some tips for using this forum.
Two pipe steam system, boiler flooding
Hello i am having trouble at a job and am hoping someone can help me out. I am dealing with a two pipe steam system. half of the radiators have thermostatic steam traps and other half are gravity. There is a condensate tank next to boiler with a 2" F&T trap. M/M #150 controller on boiler works with condensate pump and there are no coils in boiler. Boiler provides heat only. Everyday the boiler is flooding. I flushed the boiler several times and priming/surging is under control, 150, F&T trap, condensate pump, and air vents on return were all replaced. Control tree, gauge glass, surge columns, etc were all checked and cleared of any blockages. The vaporstat was lowered recently to 1.5 lbs and return lines never get hot. i was able to find some old pictures and discovered what the original setting on the vaporstat was and has been for years and there was never an issue until now. boiler currently cuts out at 4.5 PSI and cuts back in at 3. (I know this is high but this is how this system has been for many years with no problems). I am going back to this job tomorrow to follow up and see if raising pressure helped. Any help with this would be appreciated. Thank you