Welcome! Here are the website rules, as well as some tips for using this forum.
If you've found help here, check back in to let us know how everything worked out.
It's a great way to thank those who helped you.
Need some advice on a gb 142 60 replacement
Hello all, Homeowner here and not a trained technician. In 2009 I had an addition put on and a new heating system installed. I was misled in the fact that my installer knew what he was doing. 2nd year in I had some leaks at the unions which I was told by my installer I would have to fix myself. Get the picture? I got a manual for the boiler and since then have been cleaning and maintaining myself. Most important thing I realized was that the intake was sucking in the bad stuff from outside. Exhaust and intake next to each other about a foot from an inside corner. I now use interior air. No one in my area will look at it because they didn’t install it.
Last winter I was down for a couple days. Had a technician from my propane company come and he hit reset which worked for about 3 hours. Took my ohm meter and found out my return sensor was bad. I used the chart in my manual and replaced the one which the number was way off.
Now I have a little bit of water dripping from the back. Seems like it is coming from where the mount is attached in the back. When you take the bottom off the unit there is a small weep type hole up in the right back wall that was dripping into the actual fireside of the boiler. Not sure if it’s supposed to do that. A little bit of sludge in the condensation trap but not much, but I cleaned and flushed and that seemed to help. Never got a 6a though. Wondering what is back there in the flue system that would do that.
Now I’m wondering if my system is on its last legs. I know there is some damage from sucking in exhaust for a couple years. Especially the fan intake which seems to be corroded some. I know there was some chemicals added to my water on installation but I doubt the system was cleaned due to the black stuff found on my sensor.
Wondering if I should spend money on a rehab? Replace whole unit? Or go with something else. Something a little less hands on. I m not to hung up on efficiency as I am for reliability and ease of repair. Any input on brands if I go that way? Some one I know suggested a Weil-McLain “sparker type”. Thanks, Tom