Welcome! Here are the website rules, as well as some tips for using this forum.
Need to contact us? Visit https://heatinghelp.com/contact-us/.
Click here to Find a Contractor in your area.
Sizing heat pump
Jason_13 Member Posts: 304
I just did a manual J heat loss Heat gain for a house. The heat load was 32,078 and the heat gain would be 17,289. So do I do a 2 ton heat pump and the rest in electric back-up? Second choice, 1-1/2 ton heat pump and 15K in electric back-up or 2.5 ton heat pump with a little back-up?
What's the total SENSIBLE heat gain? You must size the heat pump to cover both the sensible and latent loads and consider them separately.
Usually, in a residence, the sensible is 90% or more of the total, but a typical heat pump today has about 75% sensible capacity and about 25% latent. So, you don't look at the total for the structure and then look at the total for the equipment. That's a common mistake.
Look at the sensible and latent capacity of the heat pump and make sure it's sufficient to match both the sensible and latent loads of the house.
If 17.3k btus is the TOTAL heat gain of the structure, then you're probably gonna need a 2 ton heat pump with a 10kw heat pack.Bob Boan
You can choose to do what you want, but you cannot choose the consequences.1
Your calculations help me with the heat pump installation.-3
- 121.3K All Categories
- 84K THE MAIN WALL
- 2.9K A-C, Heat Pumps & Refrigeration
- 53 Biomass
- 417 Carbon Monoxide Awareness
- 40 Chimneys & Flues
- 1.7K Domestic Hot Water
- 4.7K Gas Heating
- 119 Geothermal
- 155 Indoor-Air Quality
- 3K Oil Heating
- 56 Pipe Deterioration
- 768 Plumbing
- 5.4K Radiant Heating
- 362 Solar
- 14K Strictly Steam
- 3K Thermostats and Controls
- 51 Water Quality
- 625 Buy, Sell, Barter
- 38 Industry Classes
- 73 Job Opportunities
- 17 Recall Announcements