Welcome! Here are the website rules, as well as some tips for using this forum.
If you've found help here, check back in to let us know how everything worked out.
It's a great way to thank those who helped you.
I have a peerless boiler PT-140 and want to pair it with an indirect peerless PT-50. The piping distance between the units is 4 feet. The piping on the boiler is 1 inch and the indirect is 1-1/4. Can I use 3/4 to connect the two or should I do 1 inch?