Welcome! Here are the website rules, as well as some tips for using this forum.
If you've found help here, check back in to let us know how everything worked out.
It's a great way to thank those who helped you.
Rianne Error Code 10: what's left!?!
*sorry if this should be in another forum. Mods feel free to move this accordingly*
Read a lot of code 10 error fixes and I've tried almost everything I can think of but to no avail.
I have a RC80HPi (5 years old) and recently have been getting an error code 10.
So I've done a complete tear down:
-removed and cleaned fan
-removed and cleaned burner plate
-replaced primary hx with a new unit under warranty
-flushed the entire unit with vinegar
-cleaned out water filter
-replaced all thermal gaskets
-replaced all venting with new (original installer used incorrect galvanized steel core venting when it should have been polypropylene).
Code 10 usually exhaust/intake error but the venting is all 100% brand new (literally 2 days old), same with the hx and now the flame is perfect and super quiet... (venting is only 2-90's, one 28" horizontal run, and the 36" roof termination piece).
Prior to the swap, the venting was severely corroded and the hx had such bad build up on it I couldnt even file off the corrosion between the fins... this was obviously causing terrible exhaust/burning, and what I though would be the cause of an error code 10.
Alas, I clean and replace everything, run the shower and if the radiant floor heating kicks on (uses a separate heat exchanger) the unit kicks off and displays error code 10.
So is this a flow issue somehow? If I turn off the radiant floor heating I can shower without an issue, or vis versa. The unit is super quiet again after the new hx and venting installed.
I never had this error code 10 for the first 4 years of ownership running both radiant floor heating and shower simultaneously...
I'm at whits end with what else I can open up and replace after all the reading and tinkering I've done.
Really appreciate any help.