Welcome! Here are the website rules, as well as some tips for using this forum.
Does anyone have any experience with Dry Steam #3
? I have a customer with a single Slant Fin Galaxy/Caravan that is surging. The piping was all wrong, so we re-piped, but it still surges. We have skimmed it more times I think than all the other boilers I've skimmed combined, -all to no avail. So I called Slant Fin and they immediately said to clean with Dry Steam.
They even have an instruction sheet
in it's usage.
It used to be two boilers piped together, but it turned out that one boiler alone had sufficient BTUs for the building EDR so we mothballed the 2nd boiler.
So we are going to give it a try. Any thoughts or experiences welcome. Thanks.
New England SteamWorks
Service, Installation, & Restoration of Steam Heating Systemsnewenglandsteamworks.com