Welcome! Here are the website rules, as well as some tips for using this forum.
If you've found help here, check back in to let us know how everything worked out.
It's a great way to thank those who helped you.
What happens to heating circuit's water during off season ?
Dear Members ,
I have came across a technical problem of a heating system which composes of a non condensing wall mounted boiler ,and poly propylene pipe net work and Aluminum radiators . I examined the system which is as follows :
_ City water as a make - up - cold pressure between 1.5 and 1.6 bar - working pressure at normal operation just for providing domestic hot water for bath and kitchen is 2 bar . PH of heating circuit 8.5 and TDS 70 ppm . Clear water inside of the radiators .
When I got the system checked I found that the heating circuit ( supply and return lines ) did not have shot off valves and the heating system just turned off by its switch . The working pressure was 3.0 bar and there were some drops of water beneath of the wall mounted boiler . As I noticed that there were not valves at heating circuit lines , so I checked the radiators first . When I was trying to pen the bleeding valve of the radiator I heard a noise inside of the radiator which was look like a surge or may hammering .To my surprise , the radiator was full of air and I let the air went out until water appeared out of the bleeding valve . I saw that the rest of radiators were full of air ,and after I took the air out of the whole radiators , the manometer of the boiler showed 2 bar . i checked the make up valve which was closed and it did not let water added into the system . Thus, there are two questions , how the heating circuit water turned into air during off season ,and whether there is chemical phenomenon between aluminum and copper coil of boiler which must be balanced ?
Thank you in advance for taking the time to help me and sharing your invaluable experience with us ,
I look forward to hearing at your convenience time ,