Welcome! Here are the website rules, as well as some tips for using this forum.
If you've found help here, check back in to let us know how everything worked out.
It's a great way to thank those who helped you.
A local store owner has a 2 door and a 3 door 'zero zone' reach in coolers both running off of the same compressor using 404A. I am being asked if I can take his 2 door unit out due to him expanding a room and he's in need of the space not the cooler. The compressor is sized for the both and basically the 3 door calls and they both get cooling. Other than the compressor being oversized is there anything I'm not aware of if I cap off the 2 door and get it out of the circuit? Each reach in has its own expansion valve and defrost. Thanks in advance.