Welcome! Here are the website rules, as well as some tips for using this forum.
If you've found help here, check back in to let us know how everything worked out.
It's a great way to thank those who helped you.
Why does this set up "work"?
Did a service call for a steam boiler this week... It is a 4 sec. Weil SGO w/ a Carlin EZ gas burner. Added a Field MG1 and a spill switch that was missing. Nat gas. About 1 and 1/2 yrs old. It was piped in 1/2 CSST about 35 feet from the meter. Looking at the gas charts the pipe capacity is about 50K BTU. Burner is about 150k input. I clocked the meter and I get 148k. How can that be?