Welcome! Here are the website rules, as well as some tips for using this forum.
Need to contact us? Visit https://heatinghelp.com/contactus/.
Click here to Find a Contractor in your area.
water cooled
Options
Paul S_3
Member Posts: 1,261
on a water cooled condensor , what should the the delta t be between the supply and return pipe.....or do they vary at different tonnage??
ASM Mechanical Company
Located in Staten Island NY
Servicing all 5 boroughs of NYC.
3476924777
ASMMECHANICALCORP@GMAIL.COM
ASMHVACNYC.COM
https://heatinghelp.com/findacontractor/detail/asmmechanicalcompany
Located in Staten Island NY
Servicing all 5 boroughs of NYC.
3476924777
ASMMECHANICALCORP@GMAIL.COM
ASMHVACNYC.COM
https://heatinghelp.com/findacontractor/detail/asmmechanicalcompany
0
Comments

"Delta T"
In general I will shoot for 10 to 15*f. It will of course depend on the water temp, city, cooling tower, well etc... If you look at your head pressure it will ultimately give you that perfect temp. If I remember correctly, cw on your regulator will increase head pressure (less water). You can play with it and achieve what ever you are looking for.
Merry Christmas;
Mike T.0 
"Delta T"
In general I will shoot for 10 to 15*f. It will of course depend on the water temp, city, cooling tower, well etc... If you look at your head pressure it will ultimately give you that perfect temp. If I remember correctly, cw on your regulator will increase head pressure (less water). You can play with it and achieve what ever you are looking for.
Merry Christmas;
Mike T.0 
The Target
The target number for a watercooled condenser deltaT is 10 degrees when connected to a cooling tower (recirculating system) or 20 degrees for a wastewater system. Wastewater systems, for the most part, are not commonly used and, in many jurisdictions, are illegal.
The flow rate of water through the condenser should be approximately 3 gallons per minute per ton, so a 10ton watercooled air conditioning system will have about 30 gpm of water moving through the condenser coil. For wastewater systems, the flow rate of water is about 1.5 gpm per ton.
Hope this helps.There was an error rendering this rich post.
0 
GPM
Eugene or anybody else who can answer this.....how do i determine GPM? for example if its a 10 ton system with a cooling tower and the delta t is 10f its 30 GPM....and if the delta t is 20f i would be assuming its 15 GPM???ASM Mechanical Company
Located in Staten Island NY
Servicing all 5 boroughs of NYC.
3476924777
ASMMECHANICALCORP@GMAIL.COM
ASMHVACNYC.COM
https://heatinghelp.com/findacontractor/detail/asmmechanicalcompany0 
Use the Pump Curve
You should be able to easily obtain the "pump curve" for the pump on the system. The pump curve tells you how much water, in gpm, the pump will move in response to the "feet of head" that the pump can overcome. Most systems will have permanently installed pressure gauges on the system and the "head" can be directly obtained from the pressure difference across the pump. For every 1 psi across the pump, we get 2.31 feet of head. So, if we have 20 psi across a pump, we will have 46.2 feet of head.
Now, armed with this piece of information and your pump curve, you look up the head on the chart to obtain for flow rate in gallons per minute.
Viola!
Enjoy!There was an error rendering this rich post.
0 
Depends!
If you are looking for normal do as Proff Silberstein said. If you are looking "after the fact", you go by the what ever head press you are going to maintaine. Kinda like what Empire said only different.0 
Re: flow rate, alternate way to determine flow
Condensor mfrs will give you a pressure drop rating on condensor. Usually will have peets plugs on inlet and outlet to condensor. Check pd across condensor and you can find what flow rate is.0
This discussion has been closed.
Categories
 All Categories
 85.8K THE MAIN WALL
 3K AC, Heat Pumps & Refrigeration
 50 Biomass
 419 Carbon Monoxide Awareness
 75 Chimneys & Flues
 1.9K Domestic Hot Water
 5.2K Gas Heating
 93 Geothermal
 150 IndoorAir Quality
 3.2K Oil Heating
 59 Pipe Deterioration
 857 Plumbing
 5.8K Radiant Heating
 373 Solar
 14.6K Strictly Steam
 3.2K Thermostats and Controls
 50 Water Quality
 39 Industry Classes
 47 Job Opportunities
 16 Recall Announcements