Welcome! Here are the website rules, as well as some tips for using this forum.
Need to contact us? Visit https://heatinghelp.com/contact-us/.
Click here to Find a Contractor in your area.
I an doing my house heating system over. Goiing from steam sytem to radiant floor heating, 1 st floor .. 2nd floor hot water going to cast irom radiators.W hen istalling pex is there anything I should be aware of. .Need to use oxygen barrier, How should pex be surrported ? vertical /horizantal ? i was told that heating pannels make to much noise . Is there anything on the market that would work insfead ? Thanks for all info !hh
Hire a Pro; or
if you are determined to do it yourself get a bunch of Dan's books and start reading. I'm afraid if I were to try an answer all your questions and give you all the other information you will need to know, i'd get carpal tunnel in my fingers before I was done typing.
If you do it right though, you will have the most comfortable heat you can imagine. Don't cut any corners.
Dan, is an educator,teacher,troubleshooter, etc. Dan will tell you he is not a mechanic. It is the problems that mechanics (plumbers,fitters etc) run into, while working in the field. It's called experience. Just one piece of information is better than none. Again, thanks for you're reply.0
Ironman Member Posts: 7,119Well...
Here's a little help:
If you can route the tubing without too much difficulty, I would recommend pex-al-pex. It has an aluminum layer which makes it much firmer than regular pex and it doesn't require the amount of support that the regular does. It also has a very low linear expansion rate that is close to copper, whereas standard pex expands almost 12 inches per 100 ft. when heated a hundred degrees.
If you have rads, I would use a manifold (Rehau, Uponor, no chinese) and "homerun" each rad to the manifold. 3/4 to 1gpm is a realistic flow rate for 1/2" pex a manifold system which will give you 7500 - 10,000 btu's. That will cover most rads unless it's a really large one, then you would need 5/8 or 3/4 for that one. Measure you EDR to determine the out put of each rad and the necessary pipe size. Multiply the square footage times 150 to get the btu output.
As far as the floor goes, standard pex is easier to pull for in joist applications. Again, use a good type "A" oxygen barrier like Rehau or Uponnor. Don't use the chinese stuff, you'll regret it.Bob Boan
You can choose to do what you want, but you cannot choose the consequences.0
Thanks, for, your reply ! Happy holidays !0
This discussion has been closed.
- 121.3K All Categories
- 84K THE MAIN WALL
- 2.9K A-C, Heat Pumps & Refrigeration
- 53 Biomass
- 417 Carbon Monoxide Awareness
- 40 Chimneys & Flues
- 1.7K Domestic Hot Water
- 4.7K Gas Heating
- 119 Geothermal
- 155 Indoor-Air Quality
- 3K Oil Heating
- 56 Pipe Deterioration
- 768 Plumbing
- 5.4K Radiant Heating
- 362 Solar
- 14K Strictly Steam
- 3K Thermostats and Controls
- 51 Water Quality
- 625 Buy, Sell, Barter
- 38 Industry Classes
- 73 Job Opportunities
- 17 Recall Announcements