Welcome! Here are the website rules, as well as some tips for using this forum.
Need to contact us? Visit https://heatinghelp.com/contact-us/.
Click here to Find a Contractor in your area.
Versa Hydro CO
Sol Hydronics Member Posts: 41
I am haviing a rough start on a new 130,000 btu Versa Hydro heater. I tuned the heater using a CO anilyzer and the rough start is still there. Is it true the number I am looking for is 0 to 20 ppm on high fire, that seams low? Thanks for any help, mike
You should use
a combustion analyzer not a CO detector. With that said CO is low as a lot of these new units run at around 100 PPM. I am on the road so I do not have the manual handy for the Versa.0
I looked up
the I and O manual and found the following:
Low Fire 8.5% to 9.5
the I and O manual and the following is required:
Low Fire 8.5% to 9.5% CO2 CO 0 to 10 PPM
High Fire same CO2 CO 0 to 20 PPM.0
Thet usually send the single prong LP ignitor with the unit.
They are now shipping the pink ignitor as standard for both LP an NG
It smoothes out the ignition as it sparks to the burner.
I like high 8's Co2 on low and low 9's on high0
This discussion has been closed.
- 120.9K All Categories
- 83.8K THE MAIN WALL
- 2.8K A-C, Heat Pumps & Refrigeration
- 53 Biomass
- 416 Carbon Monoxide Awareness
- 36 Chimneys & Flues
- 1.7K Domestic Hot Water
- 4.7K Gas Heating
- 117 Geothermal
- 154 Indoor-Air Quality
- 3K Oil Heating
- 49 Pipe Deterioration
- 754 Plumbing
- 5.3K Radiant Heating
- 358 Solar
- 13.9K Strictly Steam
- 3K Thermostats and Controls
- 50 Water Quality
- 622 Buy, Sell, Barter
- 37 Industry Classes
- 70 Job Opportunities
- 14 Recall Announcements