Welcome! Here are the website rules, as well as some tips for using this forum.
If you've found help here, check back in to let us know how everything worked out.
It's a great way to thank those who helped you.
I would like to ask when siizing a A/C system and the calculations determne that the required total capacity at .70 SHR is 4.6 tons, should the system bi sized at 5 tons or drop it to 4 tons.