Welcome! Here are the website rules, as well as some tips for using this forum.
Need to contact us? Visit https://heatinghelp.com/contact-us/.
Click here to Find a Contractor in your area.
Baxi Ht 380 boiler gas pressure fault
bruce_21 Member Posts: 238
in Gas Heating
The last two times it got super cold, the boiler went off and gave a code indicating a gas pressure fault. Both times the air handler which is 75% of the heat load had been turned off. There was frost all over the outside gas regulator seen the second time, don't know about the first time. The gas company said that because the boiler was running flat out to make up the indoor temp that caused the gas pressure problem. Is this for real? How do the regulators work that a long time flow can reduce the pressure? What could be happening here?
Sounds like a vaporization problem.
Is this natural gas or propane?0
If this is Propane
it could be that the liquid is not fully vaporizing. Propane gets down to very low pressures in the tank when the temperature goes down. The boiling point of Propane is -44 degrees but vaporization can be affected when temps get down near zero. One of the solutions is to make sure the line to the Baxi is at least 3/4" pipe and has a good 10 feet of uninterrupted pipe directly to the unit.
The other thing to do is shield the second stage regulators as best you can from cold winds.
If this is natural gas then I would be very surprised if that regulator is affected by running a long time. A solution to help eliminate the freezing problem on either is to place a tee with a drip leg and fill it with "Methanol" this will help to keep the lines and regulator from freezing up The gas company or propane company should be the ones to do this.0
on Natural gas
the only freezing issues I have seen were when the roof dripped on the regulator and froze the vents shut on it. Icicles and gas regulators are not good playmates. Tin roofs of sheet metal help out until the gutter guy can get in to divert the water.Cost is what you spend , value is what you get.
cell # 413-841-6726
This discussion has been closed.
- 121.3K All Categories
- 84K THE MAIN WALL
- 2.9K A-C, Heat Pumps & Refrigeration
- 53 Biomass
- 417 Carbon Monoxide Awareness
- 40 Chimneys & Flues
- 1.7K Domestic Hot Water
- 4.7K Gas Heating
- 119 Geothermal
- 155 Indoor-Air Quality
- 3K Oil Heating
- 56 Pipe Deterioration
- 768 Plumbing
- 5.4K Radiant Heating
- 362 Solar
- 14K Strictly Steam
- 3K Thermostats and Controls
- 51 Water Quality
- 625 Buy, Sell, Barter
- 38 Industry Classes
- 73 Job Opportunities
- 17 Recall Announcements