Click here to Find a Contractor in your area.
Welcome! Here are the website rules, as well as some tips for using this forum.
Need to contact us? Visit https://heatinghelp.com/contact-us/.
Bladder-type expansion tank Best Practice
When installing a Bladder Expansion tank into a boiler piping setup, what is the best practice for piping size selection? There are 1/2" and 3/4" tanks available but it seems if the tank hags horizontal to its feed (from a T) the 1/2" could be an issue at some point. If / when the bladder breaks down and the tank fills with more water than new, it would be heavier. If 1/2 " copper is used, it seems the weight could break 1/2" piping easily if extended very far from the "T "of the feed. Having to repair this, i am thinking 3/4" is better. Are there any guidelines to review (maybe manufacturers)? Thanks in Advance!
This discussion has been closed.
- 115K All Categories
- 81.9K THE MAIN WALL
- 2.6K A-C, Heat Pumps & Refrigeration
- 38 Biomass
- 396 Carbon Monoxide Awareness
- 2.8K Thermostats and Controls
- 1.5K Domestic Hot Water
- 4K Gas Heating
- 102 Geothermal
- 145 Indoor-Air Quality
- 2.5K Oil Heating
- 37 Pipe Deterioration
- 627 Plumbing
- 4.5K Radiant Heating
- 341 Solar
- 12.7K Strictly Steam
- 44 Water Quality
- 568 Buy, Sell, Barter
- 29 Industry Classes
- 62 Job Opportunities
- 11 Recall Announcements